Use instructionsBimetallic room thermostat for heating and air-conditioning installations
Thermail,electrical and mechanical features
On opening contact,10A-250VAC (Ohmic load)
Temperature's scale adjustmentAfter almost two days from the installation,to obtain a precjse scale adjustment,measure the room temperature with a reference thermometer,placed a side the thermostat.Holding the shagrened part of the knob.turn the index with a coin,to reach the same value of the thermometer.We suggest to install the equipment at about 1.5meter from the floor and far from any heat source.
PatternB1-With N.C contact.
B2-With N.C contact and ON-OFF switch
B3-With SPDT contact(change-over)
B4-With change over contact(SPDT) and ON-OFF switch
B7-With normally closed contact on"Winter" and normally open contact on "Summer"plus "Summer-Winter"selector-switch
5)Lockpins.the lock pins for scale limitation(5)are to be detached from the base of the thermostat,They are located on the fixing holes.
The fixing of the room thermostat can be done directly on the wall by screws and nuts.
ImportantAccelarating resistance with voltage to 220-250VAC
This thermostat is provided with an accelerating resistance which must be absolutely connected in order to obtain the regulation's performances.The terminal 4 has thus to be connected to the meutral according to the diagram shown on the cover.This connection allows also the working of the pilot lamp which indicates the operation of the heating.
Inquiry - WST-7000A Thermostat
Fill out the form below and we'll be in touch soon.